Bimetallic room thermostat for heating and air-conditioning installations Thermal, electrical and mechanical features Breaking capacity on opening contact,10A-250V A.C.(ohmic load) Differential: 0.5K
TEMPERATURE’S SCALE ADJUSTMENT
After almost two days from the installation,to obtain a precise scale adjustment, measure the room temperature with a reference thermometer, placed aside the thermostat, holding the shagreened part of the knob, turn the index with a coin, to reach the same value of the thermometer,We suggest to install the equipment at about1.5mt from the floor and far from any heat source.
● ①Base ● ②Cover ● ③Cover screw ● ④Knob Lockpins, The lock pins for scale limitation ● ⑤are to be derached from the base of the thermostat.They are Located on the fixing holes. ● ⑥Index:The fixing of the room thermostat can be done directly on the wall by screws and nags.
● ①Accelerating resistance with voltage to 220-250V a.c. ● ②This thermostat is provided with an accelerating resistance which mustbe absolutely connected in order to obtain the regulation’s performances. ● ③The terminal 4has thus to be connected to the neutral according to the diagram shown on the cover. ● ④This connection allows also the working of the pilot lamp which indicates the operation of the heating.
Saipwell is a subsidiary of Saip Electric Group and is a leader in the global enclosure market. Its main business involves the manufacturing of electrical and IT enclosures, assembly of whole electrical switchgear systems and development of enclosures for use in new energy solutions